Why is my RTH6500WF Smart Series Programmable Thermostat set to Heating, but I feel Cool or Mild Air and not heat? (Or Why is my thermostat set to Cooling but I feel Heat or Mild air and not cooling?)
Check your wire.
If you have a wire in either the R or RC terminal and no wire in the other terminal (R or RC), insert the jumper wire. If you have a wire in the R terminal and a wire in the RC terminal, remove the jumper wire. *One wire? Jumper goes in. Two Wires? Take the jumper out.*
If you have a wire in the RC terminal and no wire in the R terminal, insert the jumper wire. If you have a wire in the R terminal and a wire in the Rc terminal, remove the jumper wire.
Check your configuration (referred to as the ISU [Installer Set Up]) using the user manual or installer manual.
Verify you have entered the correct System Type. For Heat pump systems, most commonly, O/B is energized in Cooling (O on cool). For Rheem or Ruud brand heat pumps, the O/B must energize on heating (B on Heat).